Water leak detection Milford, Ohio
The water leak detection service was for a 3/4″ PVC water service running roughly 100 ft between two buildings. There was a wet spot in the asphalt parking lot which gave me a rough starting point. The water pressure was 75 psi and the system produced a surprisingly strong signal when it was checked with water flowing. Compressed air was then added to the system and the noise stayed at the exact same location, providing a double check. Holes were drilled into the asphalt at several spots and helium was then introduced, which came up at the same location that the sounds were found. It’s always great when you can fully isolate a system and everything comes up at the same spot! Water leak detection in Milford, Ohio was successful!!